# 119，calculation of maximum discharge capacity (bog) under tank fire and rollover conditions (part 2) -凯时登录

﻿ 119，calculation of maximum discharge capacity (bog) under tank fire and rollover conditions (part 2) -凯时登录

welcome to"suzhou doer gas & chemical equipment co., ltd" website！

hotline： 86 512-81666096
0512-66182570

hotline

86 512-81666096
forum

now：home > news > forum

### 119，calculation of maximum discharge capacity (bog) under tank fire and rollover conditions (part 2) - doer equipment

classification：forum publishtime：2019-11-18 12:59:41

calculation of maximum discharge capacity (bog) under tank fire and tumbling conditions (part 2)

as for the calculation of maximum discharge capacity (bog) under tank fire and tumbling conditions (part 2): the calculation of liquid tumbling discharge capacity is complex. according to the provisions of standard en1473-2007, the amount of flash steam generated by tumbling should be calculated using effective specifications. if no mode is available

the flow during rolling can be calculated as:

v b =100v t

vt=v ×η×ρ/ twenty-four

where:

v b: volume of flash steam generated by rolling, kg / h;

vt: steam generated by heat doer to the increase of ambient temperature under normal operation (according to summer working condition);

5: the effective volume of the tank, i.e. the volume of liquid that can be stored in the tank at the design level, ignoring the components immersed in the liquid (e.g

volume occupied by various pipes, internal vertical ladders, etc;

η： daily evaporation rate of storage tank (based on full of pure lng);

ρ ： lng density;

5.2.4 calculation

comparing the discharge capacity under the two working conditions, the discharge capacity of the safety valve of lng storage tank shall be determined according to the larger value of the two.

the lng tank of the project is made of 20000 cubic meters of elastic felt, and the ceiling is made of pearly sand.

its parameters are as follows:

inner tank wall diameter: 36m, outer tank diameter: 26.5m

inner tank wall height: 34m, outer tank height: 24m

effective volume of storage tank 20000 m ³

the height of tank foundation is 2.2m (it is the distance from the upper surface of tank foundation to the ground, temporarily 2.2m)

lng density: 480 kg / m ³

environmental factor f 0.000275

daily evaporation rate (static evaporation rate of storage tank is calculated as 0.08% and allowance is considered)

flame height 9.15m

design liquid level h 21.2m

lng gasification latent heat 508.85 kj / kg

calculation of external fire conditions:

heat transfer in fire: h = 71000 × f × a 0.82 h n

=71000 × zero point zero zero zero two seven five ×（ π × thirty-six ×（ 9.15-2.2）） 0.82

= 71000 × zero point zero zero zero two seven five × 236.6 w

=4620w

lng gasification latent heat under pressure relief state 508.85 kj / kg

heat transfer caused by fire alone: w1 = 4620 × 3600/（1000 × 508.85）=32.69kg/h

bog generated by static evaporation under normal conditions of storage tank:

wn=v ×η×ρ/ 24=20747 × 0.08% × 480/24=166.5kg/h=331nm ³/ h；

where: v = π ×（ 34/2） 2 × 23=20747m ³， the amount of liquid contained at the design liquid level of the storage tank;

under fire conditions, the gasification capacity generated is the sum of static evaporation of storage tank and gasification capacity caused by fire alone:

wfire = w1 wn = 32.69 331 = 192.64kg/h = 363.69nm ³/ h；

rolling condition: w rolling = v b = 100wn = 33100kg / h = 41375nm ³/ h；