78，how to prevent problems in cryogenic liquid storage tanks - doer equipment
classification：forum publishtime：2019-09-19 13:33:04
how to prevent problems in cryogenic liquid storage tank
how should we prevent problems during the use of storage tanks? the following points can be referred to:
1. operators of cryogenic liquid storage tank:
understand the structural characteristics of the equipment and its pipe valve system in detail, be familiar with the dangerous characteristics of low-temperature liquid, strictly control the surrounding environmental conditions, and operate according to the safe operation procedures of low-temperature liquid storage tank. operators must be trained and qualified by the quality and technical supervision department at or above the prefecture level, and hold the pressure vessel operation qualification certificate before they can work. take labor protection measures according to the regulations before operation.
2. patrol inspection of cryogenic liquid storage tank:
during the normal use of cryogenic liquid storage tank, special personnel shall be responsible for patrol inspection. check that the pressure of the inner container shall not exceed the maximum working pressure of the storage tank. in case of overpressure, pressure relief measures shall be taken. check the status and leakage of each valve. if there is any abnormality or leakage, timely take treatment measures and properly correct the abnormality.
3. periodic inspection of warm liquid storage tank:
regularly check the vacuum degree in the jacket of cryogenic liquid storage tank. if the vacuum degree deteriorates, supplementary vacuum pumping measures shall be taken (the vacuum pumping of storage tank shall be implemented by a professional unit or the original manufacturer).
4. the cryogenic liquid storage tank shall be inspected regularly:
cryogenic liquid storage tank is a special equipment subject to national mandatory safety supervision and is listed as class iii pressure vessel, which shall be inspected regularly according to relevant national technical specifications. the safety accessories of the storage tank shall also be inspected regularly. generally, the pressure gauge, liquid level gauge, safety valve and bursting disc device shall be calibrated or replaced at least once a year. in case of various faults of cryogenic liquid storage tank equipment and accessories, find out the causes at any time, make correct analysis and judgment, and take reasonable solutions to ensure its continuous normal operation and safe use.
prev： 77，what is pressure swing adsorption nitrogen plant - doer equipment
next： 91，how to fill the storage tank with pearlite - doer equipment
- 205、lng operating procedures - doer equipment [2022-11-15]
- 205. tank classification and characteristics - doer… [2022-11-15]
- 204. brief introduction to tank development - doer … [2022-10-31]
- 204、lng vacuum cryogenic liquid storage tank - doe… [2022-10-31]
- 203、precautions for precooling of natural gas stor… [2022-10-28]
- 203、preparation before pressure regulation of lng … [2022-10-24]
- 3，successful test run of cangzhou ethylene storage… [2019-09-02]
- 2，advantages of suzhou doer large cryogenic tank … [2019-08-30]
- 1，congratulations on the success of one-time liqui… [2019-08-26]